SECTION III OPERATION UNDER USUAL CONDITIONS
ASSEMBLY AND PREPARATION FOR USE.
The refrigeration unit requires specialized unpacking ,installation, and power connection procedures. Notify unit
maintenance for installation.
Operating the refrigeration unit with the service valves improperly set will
damage the equipment. Do not operate unless you are sure it has been
properly set up for operation. Notify unit maintenance.
a . Be sure the refrigeration unit is connected to an active source of 208/230 Vac, 3 phase, 50/60 Hz electric power.
Push switches in the side condenser door frames will prevent the
refrigeration unit from operating if the side doors are open.
b. Be sure both side condenser doors (1) are closed and secured.
c. Set the remote bulb thermostat (TEMPERATURE CONTROL) (2) to the desired refrigerator enclosure
d. Place the circuit breaker handle (3) in the ON position.
e. Place the toggle switch (START/RUN, OFF) (4) handle in the START/RUN position.