4-48. SOLENOID VALVE L2 (DEFROST LINE) TESTING AND REPAIR. - Continued
Mounting hardware is not supplied with coil Screw and lock washer must
be retained for use during installation of coil.
Remove screw (4), lock washer (5), data plate (6), and coil (2).
Cut ware leads (7) if necessary and remove grommet (8).
Push wire leads (7) through grommet (8) and install grommet into coil (2).
Install coil (2), data plate (6), lock washer (5), and screw (4).
Using tags and wring diagram (fig. 1-4) connect tabs (1). Remove tags
Figure 4-43. Solenoid Valve L2 (Defrost Line)
Close right side door.
Close front bottom door
Connect power and put unit back into service.