COMPOUND GAGE (SUCTION PRESSURE) REPLACEMENT
This task covers:
Self Locking Nuts (3)
Control box cover raised and latched
Left side door open.
Loosen flare nut (1) and move copper tubing (2) over to one side being careful not to bend or kink tubing.
Remove coupling (3).
Remove three self locking nuts (4), screws (5) and compound gage (6) Discard self locking nuts.
Figure 5-28. Compound Gage (Suction Pressure)