ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
Condenser and Evaporator Fans Rotation Check (see fig. 4-7).
a. Momentarily turn MODE SELECT switch to COOL then back to OFF.
b. Verify evaporator fan expels air at high velocity out the front of the air conditioner and condenser fan expels air out
c. If fan outputs are low velocity, unit power is not wired properly, Disconnect power at source and exchange wires
connected to Control Box Assembly, terminals A and B. (See Step 4.11.6 above).
Figure 4-7. Condenser and Evaporator Fan Location
FRONT ACCESS PANELS INSTALLATION.
4.12.1 Evaporator Duct/Panel Install panel (1) and secure with six lockwashers (3), flat washer, (2), and screws (4) (see
Figure 4-8. Evaporator Duct/Panel Installation