ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
4.23 CONDENSER FAN SECTION PANEL. This task covers removal, inspection, repair/replace and installation.
Tool kit, service, refrigeration unit (Item 1, Appendix B)
Bulk gasket material (see RPSTL)
Bulk foam material (see RPSTL)
Disconnect input power to the air conditioner before performing any internal main-
tenance. Voltages used can KILL. Shutting the unit off at the control panel does not
disconnect unit power.
Disconnect air conditioner input power at source
Remove panel (1).
Check that panel (1) is not bent, cracked or punctured.
Check that gasket (4) and foam (8) are not torn, loose or missing
Check that captive fasteners (2) are not damaged or missing.
Repair consists of replacing captive fasteners (2), gasket (4), foam (8) or replacing