ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
EVAPORATOR MOTOR AND HOUSING ASSEMBLY. - Continued.
INSPECTION, TESTING, AND REPLACEMENT
Inspection, testing and replacement of the evaporator (circulator) motor and housing
assembly components is covered in the following referenced paragraphs.
Make sure rear mounting bolts (2) on the cross frame have at least 1/8 inch clearance
between flat washer and mounting bracket. This is to ensure easy installation of the
motor and housing assembly.
a. Position motor and housing assembly (6) m cabinet and align to cross-frame (1).
Figure 4-36. Evaporator Motor and Housing Assembly