ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
CONDENSER MOTOR AND HOUSING ASSEMBLY. Continued.
INSPECTION, TESTING, AND REPLACEMENT
Inspection, testing and replacement of the evaporator (circulator) motor and housing
assembly components are covered in the followmg referenced paragraphs.
Make sure rear mounting bolts (17) on the cross frame have at least 1/8 mch clearance
between flat washer and mounting bracket. This is to ensure easy installation of the
motor and housing assembly.
a. Position motor and fan assembly (11) in cabinet and align to cross-frame (7).
b. While holding cross-frame (7), slide motor and fan assembly (11) into rear mounting bolts (17) and secure two
front motor mounting bolts (14) and flat washers (13).
Figure 4-39. Condenser Motor and Housing Assembly