ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
HEAT LIMIT SWITCHES (S9 AND S10) This task covers inspection, testing, removal and installation.
REMOVAL - Continued
Stand-off hardware may differ from air conditioner to air conditioner.
b. Remove two nuts (4), lockwashers (5) and switch (6) from captive screws (9)
a. Position switch (6) in mounting position on captive screws (9)
c. Reconnect leads and remove tags.
FOLLOW ON PROCEDURES
a. Install plastic cover (7) with two screws (1), flat washers (3), and lockwashers (2).
Connect air conditioner input at source.
Figure 4-43. Heat Limit Switches (S9 and S10)