ARMY TM 9-4120-380-14
AIR FORCE TO 35E9-136-21
SOLENOID VALVES (L1 AND L2) COIL. Continued.
Replacement consists of replacmg defective cold Refer all other solenoid repair
replacement to Direct Support Maintenance.
Remove coil cover (5).
b. Tag and disconnect leads
Remove coil retainer (2) and nameplate (1)
d. Remove coil (3).
When replacing coil, perform the following: Remove one knockout and mstall grommet.
Strip and dead end wires
Fungus proof replacement coil (3) per MIL-V-173
Install new coil (3) on valve plunger (4)
Reconnect wires and remove tags.
Install coil cover (5).
Install nameplate (1) and coil retainer (2)
FOLLOW ON PROCEDURES
b. Install condenser fan section panel (paragraph 4 23).
c. Connect air conditioner input power at source