ARMY TM 9-4120-380-14
NAVY EE-000-BA-MMA-010 7053-AC
AIR FORCE TO 35E9-136-21
5.32. HOT GAS BYPASS VALVE (V). - Continued
ADJUSTMENT - Continued
If suction line pressure of 55 to 58 psig is not present, adjust valve.
Turn the adjusting stem (3) one turn to change suction by 4 psi Turn the stem clockwise to increase suction
pressure or counterclockwise to decrease suction pressure
If valve cannot be adjusted to maintain 55 to 58 psi suction pressure, replace valve and repeat Steps a
Turn unit off.
Figure 5-23. Hot Gas Bypass Valve (V4)