ARMY TM 9-4120-380-14
NAVY EE-000-BA-MMA-010 7053-AC
AIR FORCE TO 35E9-136-21
5.34 DAMPER ACTUATOR CONNECTING LINK. This task covers inspection, adjustment, removal, replace and
Tool kit, service, refrigeration unit (Item 1, Appendix B)
Disconnect input power to the air conditioner before performing any internal
maintenance. Voltages used can KILL Shutting the unit off at the control panel does not
disconnect unit power.
Disconnect air conditioner input power at source;
Check that connecting link rod (4) is not bent or damaged (see fig. 5-25).
Check that connector swivel (9), and damper operator (2) are not damaged.
Check for damaged, loose, or missing mounting hardware.
Close damper with damper adjustment actuator linkage nut (5) loose.
Open damper with 114- to 1/2-inch clearance from bottom of damper housing assembly.
Tighten damper adjustment actuator linkage nut (5).
Loosen screw (5) on solenoid connector swivel (8).
Loosen screw (3) on damper connector swivel (9).
Remove control rod (4).