ARMY TM 9-4120-380-14
NAVY EE-000-BA-MMA-010 7053-AC
AIR FORCE TO 35E9-136-21
5.35 DISTRIBUTOR. This task covers inspection, removal and installation.
Tool kit, service, refrigeration unit (Item 1, Appendix B)
Disconnect input power to the air conditioner before performing any internal
maintenance Voltages used can KILL. Shutting the unit off at the control panel does not
disconnect unit power
Disconnect air conditioner input power at source; and
If distributor lines are damaged beyond repair, replace distributor.
Check the length of the new distributor lines before cutting distributor lines to coil.
Cut distributor lines (2) to coil.
Remove distributor (1).