4-45. OUTDOOR FAN MOTOR-Continued.
(7) Push the venturi panel back toward the outdoor coil.
(8) Tag and disconnect the outdoor fan motor wiring.
(9) Slide the outdoor fan motor out of the rear of the air conditioner.
The outdoor coil fins and the fan blades can easily be damaged. Take care not to
Place the outdoor fan motor (1, Figure 4-41) into the air conditioner between the venturi panel
and the rear panel.
Slide the outdoor fan motor into the outdoor fan motor bracket (6).
Push the venturi panel (4) toward the rear panel and carefully work the fan (10) between the
outdoor coil (8) and venturi panel (4).
Mount the fan (10) on the outdoor fan motor shaft (11) so that the fan is flush with the shaft
Set screws must be aligned to the flat spots on the outdoor motor shaft and the
outdoor fan motor shaft must be flush with the fan.
Tighten the .two allen set screws (9) against the outdoor fan motor shaft.
Slide the venturi panel towards the coil (8) until it is flush while moving the outdoor fan motor (1) back into
its premarked position In the bracket Connect the wires as tagged and remove the tags.
Tighter the nut and bolt (7) on the outdoor fan motor bracket to secure the outdoor fan motor
Install the ten screws (5) to secure the venturi panel.
Install the nut (2) on the accumulator stud (3)
Install both side door assemblies. See para 4-19.
Install both front door assemblies. See para 4-17.