4-13. EVAPORATOR ACCESS PANEL
This task covers
Tool kit, refrigeration SVC
General Safety Instructions
Insulation (TM 9-4120-398-24P)
Voltages used can kill. Always
Gasket (TM 9-4120-398-24P)
disconnect power cord to air conditioner
before performing any internal
maintenance. Shutting unit off at its
control panel does not disconnect
Dry cleaning solvent (Federal Specification
P-D-680) used to clean parts is potentially
dangerous to personnel and property.
Do not use near open flame or excessive heat.
Flash point of solvent is 100F to 138F
(38 to 59 C).
(1) Remove 14 screws (1) holding the panel (2) to fhe frame.
(2) Remove panel (2).
(1) Inspect the panel for general condition.
(2) Repair by straightening bends and dents. Replace if necessary.
(3) To replace gasket or insulation:
(a) Remove as much old gasket or insulation material as possible by pulling or scraping it away frorm the