5-14. LIQUID QUENCH VALVE (cont)
(2) Check thermal bulb to see that it is securely clamped to the suction line.
(4) Replace a faulty quench valve.
(2) Unwrap insulation tubing (1) from suction line (2) so that sensing bulb (3) is exposed. Note location and
position of bulb for reinstallation.
(4) Remove liquid quench valve (4).