5-14. LIQUID QUENCH VALVE (cont)
(1) Insert sensing bulb (3) into its original position. Be sure sensing bulb is installed in the original position and is
making good metal-to-metal contact with suction line.
(2) Install insulation tubing (1) that was removed from sensing bulb and liquid quench expansion valve
connections. Secure insulation tubing with tape, item 16, Appendix E.
Install liquid quench valve (4).
Leak test all newly connected joints and those in the repaired area. (See paragraph 5-8.)