INSTALLATION INSTRUCTIONS. - continued
b. Installation Instructions. Appropriate alterations to the facility to accommodate the selected method of
installation must be completed before actual installation of the air conditioner.
(1) The following information describes a typical through the wall type installation. You may want to alter
these instructions to suit your specific application.
(a) Determine best Iocation.
(b) Make cutout in wall slightly larger than overall dimension of air conditioner.
(c) Fabricate a mounting platform or braces. Provide mounting holes to match holes in bottom of air
Two people are required to lift unit. Personal injury can result.
(2) Lift air conditioner into position. Use adequate equipment or four people to lift the unit into position.
(3) Secure unit to mounting platform or braces with four sets of mounting hardware provided with unit.
See figure 4-1, sheet 1, for cross section view of bottom mounting holes and hardware.
Death on contact may result if personnel fail to observe safety precautions.
For safe operation, connect a 10 AWG (minimum) ground wire to the air
conditioner external ground. Make sure that shelter is properly grounded.
(4) Connect a 10 AWG (minimum) ground wire from shelter ground to air conditioner external ground. The
air conditioner external ground connection point is located on front left side of control module. (See figure 4-1,