INSTALLATION INSTRUCTIONS. - continued
(5) Fill in and seal area around the air conditioner to prevent loss of conditioned air. Flexible plastic foam
and pressure sensitive tape may be used.
(6) Fabricate an input power cable using the connector supplied with the air conditioner. (See appendix F,
(7) Remove the condensate drain plug from lower left rear corner of the unit. If air conditioner is mounted
in a location where water pouring from this drain will be objectionable or create a hazard, connect a drain line at this
point. The fitting used must have a male 1/8 -27 NPT connection to unit. Hose, rigid pipe or tubing can be used
to direct drain water to a more desirable disposal location.
(8) Connect power cable to a 208 volt, 3-phase, 50/60/400 hertz or 230 volt, single-phase, 50/60 hertz
input power source.
For more information on air conditioner installations, refer to MIL-HDBK-116
Environmental Control of Small Shelters.