FRESH AIR DAMPER AND ACTUATOR. - continued
(22) Put damper (7) in center position and tighten screw (1).
(23) Check actuator plate (19) for smooth operation.
Connect power at power source.
LOGIC BOX ASSEMBLY (LGC1).
This task covers:
Refrigeration Unit Service Tool Kit
Logic Box Test Fixture
Use disconnect switch (NOT POWER
CABLE) to disconnect power to unit.
Damage to cable connector pins will
result if cable is used.
Logic Box Assembly
Disconnect power from power source,
schematic and parts list to fabricate one.
(1) if a complete test fixture is being used, connect it to a standard convenience outlet and be sure the
POWER switch is in the OFF position. (See figure 5-2.) if a test fixture was fabricated per schematic
120.5 volts dc. Be sure it is turned off and connected to the test fixture where indicated.