This task covers:
Refrigeration Unit Service Tool Kit
Use disconnect switch (NOT POWER
CABLE) to disconnect power to unit.
Damage to cable connector pins will
result if cable is used.
Disconnect power from power source.
Check receiver (1) for dents or any other signs of damage. Replace if damaged.
(3) Remove four screws (2) and two retaining straps (3).
(5) Position new receiver (1) in place and braze two lines (4) to condenser coil (5). (See paragraph 5-14.)
(6) Secure receiver with two retaining straps (3) and four screws (2).