3-9. REMOTE MOUNTING OF CONTROL PANEL. This paragraph is applicable only when the control panel is to be
remote mounted. If the control panel is to be removed from the unit and installed in a remote location, follow instructions
of this paragraph. For interconnecting cable circuit designations and required power input information, refer to Electrical
is used in operation of this equipment
DEATH ON CONTACT
may result if personnel fail to observe safety precautions.
Never work on electrical equipment unless there is another person nearby who is
familiar with operation and hazards of equipment and who is competent in
administering first aid. When technician is aided by operators, he must warn them
about dangerous areas.
Whenever possible, input power supply to equipment must be shut off before
beginning work. When working inside, after power has been turned off, always
ground every part before touching it. Be careful not to contact high voltage
connections when installing or operating this equipment.
Whenever nature of operation permits, keep one hand away from equipment to
reduce hazard to current flowing through vital organs of body. Do Not operate
equipment without all guards, louvers, and covers in place and tightly secured.
Be sure input power is disconnected before doing any work inside the air
a. Remove fourteen screws (1) and front cover (2) from top of unit.
b. Remove eleven screws (3) and eleven washers (4) and pull access panel (5) away from front of unit (6).
c. Remove two nuts (7), two flat washers (8), wire (9), and two lock washers (10), and then disconnect wiring
harness connector J6 from connector P6 on the back of the control panel assembly (11).
d. Loosen screw (12) from center of control panel assembly and remove control panel assembly fro m air conditioner.