3-9. REMOTE MOUNTING OF CONTROL PANEL. -Continued.
e. Mount the control panel assembly (11) in the desired location by tightening screw (12) through the center of the
control panel assembly and into a 1/4-20 tapped mounting hole prepared at the new remote mounting location. Care
should be taken to locate the control panel assembly and sensing bulb where there will be an accurate temperature
f. Fabricate an interconnecting cable/harness of the required length to connect J6 to P6 with two lock washers (10),
wire (9), two flat washers (8), and two nuts (7) on the back of the control panel assembly (11) and install this new cable
assembly in accordance with local installation policies. (Refer to Appendix F for interconnecting harness fabrication
g. Install access panel (5), eleven washers (4), and eleven screws (3).
h. Install front cover (2) and fourteen screws (1).
3-10. INSTALLATIONS THAT REQUIRE REMOVAL OF FABRIC COVER. Some installations require removal of the
condenser side fabric cover. This generally applies only when air conditioner is positioned inside with condenser and
fresh air openings ducted to the outside. (Refer to Figure 3-3).
If air conditioner is to be installed with condenser side (rear) exposed, the fabric
cover should be left in place if possible.
a. Remove three screws (1), three flat washers (2), and three lock washers (3).
b. Carefully remove the fabric cover (4) from unit (5). Store the cover in a safe place for future use.
c. Reinstall three lock washers (3), three flat washers (2), and three screws (1) into unit (5).
Figure 3-3. Fabric Cover Removal.