4-27. LIQUID SIGHT INDICATOR (SIGHT GLASS).
This Task Covers:
Tool Kit, Service, Refrigeration, Unit (Item 1, Appendix B)
Air conditioner shut down and cool.
Condenser fan scroll nearest liquid sight indicator removed (see para. 4-14).
(1) Remove two screws (1), two lock washers (2) and mounting plate (3).
(2) Remove liquid sight indicator (4) from unit.
(1) Position liquid sight indicator (4) on related tubing.
(4) Secure mounting plate (3) and liquid sight indicator (4) to unit with two screws (1) and two lock washers (2).