The FDECU cover is heavy. Be sure the cover retaining rod is in place and
properly secured with hair pin cotter. Injury can occur if cover drops.
4.58.2 Remove remote control box (1) from inside shelter and route back to FDECU. Seal any opening made in shelter.
If the bracket (2), used in the unit for storage, was used to mount the remote control box inside the shelter, remove it and
install back into the unit.
Rotating parts and lethal voltage levels are used in operating the FDECU. Be sure
power source is disconnected. Injury or death can occur if connected to power
188.8.131.52 Loosen eight captive screws (3) and carefully pull the electrical assembly (4) out.
184.108.40.206 Turn to release three latches (5) and open power box assembly cover (6).
220.127.116.11 Remove two nuts (7), lock washers (8), flat washers (9), screws (10), and flat washers (11). Install bracket (2)
and align mounting holes. Secure with hardware just removed.
18.104.22.168 Close power box assembly cover (6) and turn three latches (5) to secure.
22.214.171.124 Carefully slide electrical assembly (4) into frame. Be sure no cables or wires are pinched. Secure with eight
captive screws (3).
4.58.3 Place remote control box (1) in storage position on bracket (2) then secure with two wing nut fasteners (12).
4.58.4 Coil cable (13) and secure with fastener straps (14).