ternator) regulator undergoing test
(1) Turn all switches beneath the meters
on the regulator mounting bracket and
on the test stand to the maximum read-
connect it to the regulator binding
ing position, all rheostats fully coun-
posts (10, fig. 15) and the ac/dc sys-
terclockwise, and all on-off toggle
tem binding posts (9, fig. 15) using
switches to "OFF" position (some
applicable harnesses and lead as
toggle switches have center position
(pulley- or direct-driven) of known
(6) Remove the rectifier mounting bracket
serviceable condition (pars.
assembly from the rectifier compart-
e) on the low speed driving head (5,
ment and mount a rectifier of known
94 or 95)
as shown in
s e r v i c e a b l e condition (par.
(Refer to TM 9-7003 or TB 9-2300-
206-15 for checking rectifier) on the
rectifier mounting bracket assembly
as applicable for the type (pul-
ley- or direct-driven) generator (al-
(7) P l a c e the rectifier and mounting
ternator) use, (2) above.
bracket assembly, (6) above, in the
rectifier compartment as shown in fig-
using applicable cable harnesses (fig.
(8) Lower or raise the rectifier and mount-
ing bracket assembly so the rectifier