(b) The position of switches and con-
is removed, (when necessary for
access to the control units for set-
( 2 ) through (4) below are listed
ting adjustment) and each indi-
each of these items in the positions
( a l t e r n a t o r ) regulator is tested for
of the table
indicated in column
performance as specified by manu-
b e f o r e tests are started.
f a c t u r e r and/or pertinent publica-
(2) Voltage regulator ground test.
covering t h e g e n e r a t o r
(a) Connect two test leads to the test
i n d i c a t o r binding posts as shown
and specification settings are given
i n (2) through (4) below.
Testing the voltage regulator of Leece-Neville Company generator (alternator) regulator for grounds.