Figure 1. MSD Wet Well
6. If the residual chlorine test requires chlorine adjustment, perform the chlorinator feed tube adjustment proce-
dure in this work package.
CHLORINATOR FEED TUBE ADJUSTMENT
The chlorinator can be adjusted while online.
1. To provide the maximum chemical dose, fully insert the feed tube (figure 2, item 1) into the body
(figure 2, item 2) until it locks into position between the ribs in the flow deck (figure 2, item 3).
2. To reduce the chemical dose, rotate the feed tube (figure 2, item 1) clockwise 1/4 of a turn. Rotating the feed
tube raises the tube approximately 1/8" and reduces the chemical dose.
Figure 2. Chlorinator Adjustment
END OF WORK PACKAGE