4-47. SOLENOID VALVE L1 (LIOUID LINE) TESTING AND REPAIR - Continued
Mounting hardware is not supplied with coil Screw and lock washer must
be retained for use during installation of coil
Remove screw (4), lock washer (5), data plate (6), and coil (2)
Cut wire leads (7) if necessary and remove grommet (8).
Push wire leads (7) through grommet (8) and install grommet into coil (2).
Install coil (2), data plate (6), lock washer (5), and screw (4)
Using tags and wiring diagram (fig 1-4) connect tabs (1) Remove tags.
Figure 4-42. Solenoid Valve (Liquid Line)
Close right side door
Close front bottom door
Connect power and put unit back into service.