HIGH VOLTAGE exists in electrical system of shop. All electrical inspections,
repairs, or replacements will be performed with power OFF and only by a
qualified electrician. Serious shock hazards exist which could result in INJURY
OR EVEN DEATH to personnel.
CONNECTING PDB TO GENERATOR (IF NECESSARY)
This procedure is required only if power is not available. Only a qualified
electrician should attempt to connect PDB to generator.
PDB and Pigtail are supplied by unit. Refer to TM 9-6150-226-13 and/or TM 9-
6150-226-23P for additional information.
1. Ensure all circuit breakers on PDB are in the OFF position.
2. Ensure pigtail is connected to PDB.
3. Connect pigtail wires to generator lugs by connecting black wire to lug L1, red wire to lug L2, blue or orange
wire to lug L3, and white and green wires to lug L0 on generator.