5-7. CONDENSER VANVE AXIAL FAN MAINTENANCE
This task covers:
Tool Kit,-Service Refrigeration Unit,
Cropping Tool, Appendix B. Section III, Item 3
Refer to TM 9-4120-408-24P for part numbers of items
to be replaced.
Power Supply, 28v, Appendix B. Section III, Item 8
Two personnel are required for lifting the condenser
Regulator, Nitrogen, Appendix B. Section III, Item 9
Section III, Item 16
Leak Detector, Appendix B. Section III, Item 17
Condenser Assembly removed from shelter, refer to
applicable system technical manual.
Upper Condenser Protective Grille and
General Safety Instructions
Do not work on equipment without following standard
shop safety precautions.
Do not work on equipment with
power connected. Electrocution
hazard is present. Failure to obey
this warning may result in death
or serious personal injury.
Dehydrator must be replaced every time the air conditioner lines are exposed to the
atmosphere. Failure to obey this caution may result in equipment damage.