5-30. CONDENSATE DRAIN PAN MAINTENANCE
This task covers:
Section III, Item 1
Refer to TM 9-4120-408-24P for part numbers of items
Recovery and Recycling Unit, Appendix B, Section III,
to be replaced.
Regulator, Nitrogen, Appendix B, Section III, Item 9
General Safety Instructions
Do not work on equipment without following standard
shop safety procedures.
Dehydrator must be replaced every time the air conditioner lines are exposed to the atmosphere.
Failure to obey this caution may result in equipment damage.
(1) Remove all conductive caulking from condensate drain pan (1) and evaporator housing (2).
Ensure all fungus, mold, and mildew is removed from condensate drain pan. Failure to obey this
warning may result in serious personal injury.
(2) Clean condensate drain pan (1) as required.
(1) Inspect condensate drain pan (1) for damaged welds, missing or damaged fitting, and damaged condensate level
warning switch mounting bracket.