Table 2-1. Operator/Crew Preventive Maintenance Checks and Services (Continued)
Within designated interval, these checks are to be performed in the order listed.
B - Before
D - During
ITEM TO BE INSPECTED
Procedure: Check For and Have
Equipment is Not
Repaired as Needed
LEVEL CONTROL SWITCH
During refueling operation, insure that level
Fuel flow does not
control switch functions properly by allowing
stop when tank is full.
fuel to enter tank and shuts off fuel flow when
tank is full.
Check drain button (5) operates
Drain button does not
properly and does not stick in the
operate or sticks
in down position.
GASKETS AND PACKINGS
Visually check converter for leakage, paying
Class II or III
particular attention to housing interface with
leaks are found.
tank opening (1) between housing and adaptor
plate (2), between adaptor plate and fuel press
adaptor (3), and between housing and adaptor (4).