ARMY TM 9-4120-380-14
NAVY EE-000-BA-MMA-010 7053-AC
AIR FORCE TO 35E9-136-21
5.38 VIBRATION ELIMINATORS (VE1 AND VE2. This task covers inspection, removal and installation.
Tool kit, service, refrigeration unit (Item 1, Appendix B)
Disconnect input power to the air conditioner before performing any internal maintenance.
Voltages used can KILL Shutting the unit off at the control panel does not disconnect unit
Disconnect air conditioner input power at source;
Inspect vibration eliminators (4) and (5) for evidence of leaks or damaged lingo (see fig, 5-29).
When removing suction and discharge vibration eliminators, avoid coming in contact
with coil to avoid injury to personnel and to reduce fin damage on the coil.
If suction valve vibration eliminator (5) is to be replaced, remove compressor (paragraph 5.37).
Debraze at joints (2) and (6) for suction vibration eliminator (5) (paragraph 5.12)
Debraze at joints (3) and (1) for discharge vibration eliminator (4) (paragraph 5.12).
Remove vibration eliminator (4) or (5).