RECTIFIER (CR1) AND CAPACITORS (C1 AND C2).
This task covers:
Refrigeration Unit Service Tool Kit
Use disconnect switch (NOT POWER
CABLE) to disconnect power to unit.
Damage to cable connector pins will
result if cable is used.
Disconnect power at power source.
Check rectifier (1) and capacitors (2) and (3) for general condition and broken or missing terminals or leads.
Replace if damaged.
(1) Using a tool with an insulated handle, short across capacitor terminals to discharge them.
(2) Tag and unsolder wire leads and capacitors (2) and (3) from rectifier (1) terminals. (See paragraph 4-24.)
(3) Remove screw (4), lock washer (5), flat washer (6), and rectifier (1).