5-23. EVAPORATOR LOW PRESSURE SWITCH MAINTENANCE. (Continued)
Follow on maintenance:
5-24. EVAPORATOR SINGLE ROW TERMINAL BOARD MAINTENANCE.
Thin task covers
Tool Kit, Service Refrigeration Unit,
Recovery and Recycling Unit, Refrigerant,
Refer to TM 9-4120-408-24P for part numbers of items
to be replaced.
Section III, Item 9
Manifold Gage, Charging and Testing, Appendix
Wiring Harness, A106J1, leads disconnected, paragraph
Condensate Level warning Switch leads disconnected,
General Safety Instructions
Do not work on equipment without following standard
shop safety precautions.
Dehydrator must be replaced every time the air conditioner lines are exposed to the atmosphere. Failure
to obey thin caution may result in equipment damage.
. Remove two nuts (Figure 5-20, 1), lock washers (2), flat washers (3), screw" (4), single row terminal
board (5), and marker strip (6). Discard lock washers (2).
(1) Inspect single row terminal board (5) for cracks, broken, missing, corroded or dirty contacts on the terminal
(2) Inspect all mounting hardware for damage.
Change 1 5-57