5-25. EQUALIZER LIKE TUBE ASSEMBLY - MAINTENANCE.
This task cover:
Tool Kit, Service Refrigeration Unit,
Recovery and Recycling unit, Refrigerant,
Refer to TM 9-4120-408-24P for part
Manifold Gage, Charging and Testing,
numbers Of items to be replaced.
General Safety Instructions
Do not work on equipment without following standard
shop safety precautions.
Dehydrator must be replaced every time the air conditioner lines are exposed to the atmosphere. Failure
to obey this caution may result in equipment damage.
Remove. Loosen two flare nuts (Figure 5-21,
1) and remove equalizer line tube assembly (2).
Inspect equalizer line tube assembly (2) for cracks, rooted, bends. damage, or damaged flare nuts.
Refer to Appendix F. Figure F-16 and repair equalizer line tube assembly (2).
Position equalizer line tube assembly (2) in evaporator assembly (3) and using two flare nuts (1) secure it to
thermoexpansion valve (4) and suction line tube assembly (5).
Follow on maintenance:
Change 1 5-59